You are here: / Home
Reduction of primary noise sources of fans
Dr.-Ing. Ralph Krause
...using numerical and experimental methods with contra-rotating axial fan
Focus of the research project
The project aims at the development of a low-noise contra-roating axial fan stage by conserving the high power density with respect to the acoustically demanding operating conditions. The noise reduction is achieved by a special design of the blades as well as braces with contact to the air flow. The potential of noise reduction is obtained by reducing
- the specific sound power level and the improvement of
- the psycho-acoustic parameters.
Reasons for noise sources
Sound sources can be characterised by the following figure according to Bommes (1994) and Carolus (2013).
Summary of noise source on fans (green: important noise sources at axial fans)
Pressure fluctuations due to transient forces at the blades are the main reasons for noise propagation. All further reasons (secondary sources, tertiary sources and stationary blade forces) are of minor importance or can not be influenced by fluiddynamical changes.
Due to the noise sources, different activities can be taken into account for reducing the noise propagation at fans. According to figure 2, following noise sources shall be in the focus of the research:
- leading edge noise
- trailing edge noise
- instability waves
- periodical separations
- large scale separations
- turbulent boundary layer
- tip vortices
The research project aims at the application of noise reducing activities of technical and psycho-acoustical manner with a contra-rotating fan by maintaining a constant high-level power density. The whole potential of noise reduction is estimated to be
- 10 dB .
|specific sound power level||43 dB||-5...-7 dB|
|Psychoakustik||no values||-3...-5 dB (estimated)|
The potential of noise reduction is divided into:
- the reduction of the specific sound power level and
- the improvement of the psycha-caoustics.
Throughout the research project, the following applications will be investigated:
- serrations at the trailing edge a the first whell
- sinusoidal structures at the leading edge of the second whell
- porous structures at the first whell
- serrations at the trailing edge of the first braces
- sinusoidal structures at the leading edge of the second braces
- porous elements in the shroud for reducing tip vortex noise
Following techniques will be employed to obtain a solution:
- numerical calculations (LES, RANS, URANS)
- acoustical calculations
- experiments (reverberation room, acoustical camera, PIV)
You are interested? Get in contact with us.
Kercher M, Heimann J, Puhl C, Oeckel K, Friebe C and Krause R (2018), "Application of Rotational Beamforming Algorithms on fast Rotating Sound Sources", 7th Berlin Beamforming Conference 2018.
Kerscher M, Heilmann G, C.Puhle, Krause R and Friebe C (2017), "Sound Source Localization on a Fast Rotating Using Beamforming,the 46th International Congress and Exposition on Noise Control Engineering, Hong Kong, China", INTER-NOISE , HONG KONG. , pp. 626 (1-8).
Krause R, Friebe C, Kerscher M and Puhle C (2018), "INVESTIGATIONS ON NOISE SOURCES ON A CONTRA-ROTATING AXIAL FAN WITH DIFFERENT MODIFICATIONS", FAN 2018; International Conference on Fan Noise, Aerodynamcis, Applications and Systems, 18. – 20. 04. 2018, Darmstadt, Germany. , pp. 1-12.
All-in-one device for freeze-drying and production of biomaterial
with automated freezing and sterilisation option
Certification of efficient air conditioning and ventilation systems through the new "indoor air quality seal" for non-residential buildings
Good news for building owners, architects, general contractors and specifiers:
Investigation according to DIN EN ISO 14903
These tests according to DIN EN ISO 14903 are possible at ILK Dresden